Is your water heater leaking or just not working so there is no hot water? Is it old and do you need a new one? When should I replace a water heater? Can I install a water heater myself? Who to contact for the replacement?
Answers to these and other similar questions are what you will find in this DIY guide and also learn how to replace a gas water heater in 10 easy steps. See how long does the gas water heater last, what are the reasons for the replacement and when is the best to install a new one. Learn how to deal with a natural, propane gas and plumbing work, so you can save money and install a new unit properly and safe.
Replacing a water heater is the last thing you want to hear when having a problem with the hot water - leaking, corrosion or element failure are the main reasons for replacing the old and installing a new unit.
As most of us, you will try first to fix the problem. If your gas heater is leaking you will try to find where the leak is coming from and fix it. If the tank lining is corroded because of the aggressive hot water action, the only thing you can do is to replace a water heater.
If your gas water heater is not producing enough hot water, it may suffer from sediment buildup (hard water) and rust. The recommendation is to drain and flush your gas appliance, but if it doesn't work... water heater replacement is what needs to be done. If you have a very old water heater, buying a new unit can be a good thing. New units are more energy efficient, they are equipped with the FVIR system, which protects the unit and the property from the accidental fire of the flammable vapors and is less prone to corrosion.
If you were happy with the performance of the old unit, hot water production, recovery rate, efficiency; try to match features when buying a new unit.
I think this is the easiest and safest way to replace a water heater, a tank unit that is using propane / LP or natural gas.
Important: Take precautions when working with gas, it is really dangerous if gas is leaking. For the successful work, you need basic plumbing and gas skills and the right tools.
If you live in Canada or US and would like to know how much does it cost to replace a gas water heater, or require a professional, contact networx.com and get up to three FREE estimates from the local plumbers.
Your very first step in water heater replacement is to drain water from the tank. In short:
A step-by-step guide on how to drain water from the gas tank-type water heater is described here.
On the atmospheric-type gas water heaters, the vent pipe is made of sheet metal segments connected to each other with the screws.
Separate the flue from the draft hood, and remove only those elements to free up some space for an easy access. Mark the elements if needed so you will know how to bring them back and in the right order.
Clean the vents off if they are covered with the dust and other residues but be careful not to bend or damage any part of the duct. Replace the flue pipe if it is corroded or if it has lost its functionality.
Power and direct venting are also easy to remove; first uses a plastic pipe that is attached to the heater's exhaust adapter, while the direct type often uses a metal flexible pipe and adapter which can also be easily disconnected. If you are not sure what is considered as a proper venting and how to remove exhaust gases safely from a home, check out this article.
Close the gas valve on the main gas supply line and gas control valve on the unit. To confirm that the gas line is disconnected properly, check the pilot light, it should be out.
If the gas unit uses a flexible gas line or copper pipe use the adjustable wrench to disconnect it (unscrew the nut) from the gas control valve.
If the gas line uses the rigid pipes (depending on local regulations) loosen the line unions using two wrenches. Disassemble the threaded "TEE" and "drip leg".
You must be very cautious during the water heater replacement and when dealing with any gas work. Even a small thread damage can produce gas leaking. If you accidentally damage the gas control valve... here is the guide how to replace the valve.
Water lines are located at the top of the water heater. An incoming cold water pipe has a blue ring while the hot outgoing pipe has red.
If your gas appliance is using the rigid galvanized pipes, simply open the unions close to the unit by using the adjustable wrenches.
If using the copper solid pipe, cut the pipe just below the shutoff valve. Be sure to have the cut straight and take all the particles out. For a new installation, prepare the copper pipe for soldering by removing burrs, polishing and applying soldering paste.
Plastic CPVC pipes are also easy to use and remove.
The simplest way is if the unit uses the flexible copper connectors as it is very easy to disconnect it with a wrench. The use of such connectors depends on the local codes and manufacturer's recommendation.
Once the flue pipe, gas and water line are removed or disconnected from the water heater, proceed to the unit's removal.
Make some room for the new gas heater, by moving the old unit out. Keep in mind that the old heater can be heavy especially if it had a problem with the sediment buildup, so use wisely all the help you need, dolly cart for example.
If you need a help to choose the right gas heater, there are some good information (a guide actually) how to choose the heater, money saving tips, reviews of different brands and manufacturers here, or if using the navigation bar with links to Rheem, AO Smith, and other manufacturers.
Bring the new unit in. If the size and features are the same, the odds are you don't have to adapt the water line, gas line or duct line.
At this point, you are half done with your water heater replacement, you just have to put everything back, but in reverse order.
First, check the local codes, manufacturer's requirements and recommendations what type of the water line you can install (CPVC, copper or iron).
If the solid copper pipe is the best option, use it. Connect the home plumbing and water heater combining the copper pipe and correct copper fitting, soldering to each other.
If you have to work with the galvanized pipe, use a wrench and union to make a connection, but first make sure to seal the threads.
The easiest way is using the flexible copper or stainless steel connector.
The temperature and pressure relief valve or short TPR valve, as the safety element, must be installed on the heater. Most of the time it is built-in by the manufacturer, but can also be provided disassembled.
Hook up the gas line using a rigid (iron) pipe, usually called a black pipe, or flexible connection (check local code). Use the pipe joint compound or Teflon tape for all male type threads. Take the gas "T" fitting with a capped nipple at the bottom and use a wrench to tighten it to the pipe, and connect it to the gas valve on the heater.
The upper end of the nipple will be connected to the gas line and bottom to the drip leg, so it can collect sediments, dirt, and moisture from either natural or propane gas.
Keep in mind that any work on the gas line and devices should be done by the licensed professional. You can contact one here.
Once done with the gas line, open the main gas valve and use soapy water and a brush. Apply soapy water on all connections and if the bubbles appear, the gas is leaking.
The solution for this problem is easy, you have to tighten the connection. If gas is still leaking, turn off the gas valve, dismantle all the fittings, clean it carefully - especially treads, seal it, don't over tighten and run the test again.
Reusing the old vent pipe makes sense as long as it isn't damaged and you didn't have any problem with the performance with the previous heater. If the size of the unit is the same and if the flue pipe is not broken, has no cracks or rust elements, and there are no changes in bends and diameter, there is no need to get a new one.
Once the flue is cleaned from the dust, residues, sediments, and rust install it in the same order those marked segments, and with the same inclination. Don't forget to put screws back, to connect the flue pipes together.
This is the last step in water heater replacement mini guide. Excited?
It wasn't that hard, right?
Turn the water valve ON and open the nearest hot water tap so the air is not trapped in the heater's tank and water lines. When the water flows freely close the tap - the air is gone.
Start the unit by lighting the pilot or activating the igniter on the gas control valve, by switching to the ON position. You should be able to hear the ignition sound. Ignition procedure is usually described on a sticker.
Or, you can read the article how to light a water heater and find the detail instructions. Keep in mind that most of the manufacturers have a similar procedure for lighting/relighting the pilot light. Pilots are easy and safe to light and don't require any special tools or a professional.
As it can be seen, gas water heater replacement isn't complicated. These are the basics on how to remove the old and install a new water heater. Keep in mind that an average lifespan of the tank-type gas water heater is 8-12 years, but the replacement can take place sooner, if, for example, you want to install better performing and efficient unit or the irreparable problems occur. The cost for DIY replacement is a few hundred dollars but depends on the complexity. If you are not sure how to do it, do not have the right tools and skills, higher a plumber.