Ignition problems on AO Smith Vertex GDHE-50 water heaters and how to troubleshoot? This troubleshooting guide will provide useful repair tips, info on checking the proper operation, testing, how to diagnose and fix a water heater if there is no hot water due to no ignition, ignition failure and no flame at the burner.
To locate and identify the cause of the ignition failure problem, let’s first check out some of the main parts. AO Smith Vertex GDHE-50 is equipped with the Control System that regulates water temperature inside the unit, heating cycle, ignition and performs a diagnostic check during the water heating cycle. If there is a problem with the system, such as the mentioned ignition issues, the self-diagnostics test will detect the problem and display the message on the LCD screen, and stop the heating process.
The flame sensor is part of the burner assembly – together with the igniter, burner and wiring harness. A gas blower and burner assembly must be removed before servicing the flame sensor and igniter.
The flame sensor is the metal rod partially enclosed in a ceramic insulator and connected to the control board by the wiring harness. The bare, metal part of the flame sensor is in contact with the burner flame and at a specified distance. The element is electronically controlled by measuring the flame sensing current which ensures that the gas is flowing to the burner and is burning safely. The burner must be grounded if you want to have an uninterrupted current flow from the flame sensor to the burner.
The igniter type used to light the gas on the burner is the hot surface igniter type (HSI). The Control System powers the igniter (120 VAC) and monitors the amperage through the element. More Amps higher the temperature of the igniter surface is. The hot surface igniter is more reliable and can last longer than the pilot light, but its life expectancy depends on the usage.
Over time and due to regular wear, the igniter surface temperature decreases, as the electrical current, due to increased resistance, declines. The igniter must be replaced if the testing shows that the resistance value is much below the design values (check the manual) or it is an open circuit with an infinite ohm.
The ignition failure is one of the problems related to the malfunction of the above elements. The water heater has failed to ignite the gas burner. The ignition failure fault message found on the LCD screen will be displayed if the flame sensor didn’t confirm the flame presence at the burner or the flame sensing current didn’t meet the requirement – equal or above 1.0 µA.
The control system will try to ignite the gas on the burner up to three times, and if nothing happens after that, the system will lock out, and the "Ignition Failure" fault message will display on the LCD screen. The S1 dipswitch is factory set for 3 trials but can be configured between 1 and 3 trials.
To fix the problem, do the following;
Things to check before servicing include proper installation of the water, gas, electrical and venting system, the gas pressure in the recommended range, correct polarity and unit grounding.
Note- The above examples describe the main causes and solutions of the ignition failure. Do not try to perform any of the work described above if you are not qualified for this work. It is better to call a professional plumber or technician who is licensed and certified.