Learn how to remove sediments and mineral deposits from electric and gas water heaters. Find out what is the cause, about symptoms and how to troubleshoot to prevent the element failure, increase the performance and efficiency. Check out what is the best way to prevent the sediment build-up problem.
Sediments are mineral deposits that are found in any water heater storage tank; no matter is it a newer model or an old one. Mineral deposits are usually found at the bottom of the tank, on the heater’s elements, and especially when water is heated. The amount of deposits depends on the water type, its hardness, the presence and efficiency of the self-cleaning system.
Sediments are found in water in solid shapes, like sand or particles coming from the well or municipality system and which are not dissolved. Even pieces of the limescale build-up and rust.
Rust deposits, for example, are the result of the aggressive water action, when the tank starts corroding, due to lack or failed rust protective elements like anode rod or metal tank lining.
The sediments in the plumbing and water heaters will eventually cover the elements such as electric heating elements, gas burner, also clog the valves, faucets or reduce the water flow. All these problems can lead to lower efficiency and performance, reduced power output, even shorter element life; and are a good sign that the water heater needs flushing and draining.
For example, popping or sizzling noise is coming when water is trapped under the limescale, next to the heating elements.
Even if the noise disappears due to change in water scale structure, that doesn't mean that tank flushing is not necessary; be aware that tank or heating elements can fail.
Lime buildup increases when the water is heated; with increased temperature and water hardness, higher usage and increased heating surface. Deliming is, therefore, a necessary operation that has to be included in the regular maintenance and service.
Sometimes, the problem with sediments is significant, making the tank hard or not even worth cleaning, so buying a new electric or gas appliance is the only option.
If your water heater is not performing as it should, or you hear the unusual noise inside the heater, as mentioned above, you have to act accordingly. Deposits are often loose, which makes them easy to remove. If you wait for too long, water scale can harden and make it tougher to remove.
One of the solutions to get rid of the sediments from the tank type heater, including the limescale, is to dissolve the residue with the delimer solution, like phosphoric acid or vinegar, and flush it out. Vinegar, for example, can be poured in through the opening once you remove the anode rod for checking and replacing. Let the vinegar sits for several hours to dissolve the limescale, and then flush it out.
Manually scraping of some elements is another fix, but it is time-consuming, and it is harder to reach some parts and clean it in full.
Decreasing the hot water temperature can slower the formation of limescale, while installing the water softener can significantly reduce the hardness of water, and the anode rod can be affected.
For all these reasons from above, prevention is the way to go.
Tools that you need to do the job:
Note: In a case of the electric water heaters, if the water is emptied from the tank and if the power is turned ON, the heating element is exposed to the air, which will eventually burn out the element. So turn the power OFF. Also, it is important to have the tank full of water, bleed out all the air from the tank, using the TPR valve and hot water tap. When the hot water tap is open, water should be running continuously.
Below are examples, how some big water heater manufacturers in North America, are fixing problems when the sediment and limescale deposits occur in the tank.
DynaClean is the patented automatic cleaning system from AO Smith water heating company. Thanks to the specifically designed dip tube that creates cold water turbulence in the tank, sediments and lime build-up, accumulated from the hard water are significantly reduced.
Hydrojet Total Performance System is the patented system from Bradford White that fights mineral build-up in the tank while extending the first-hour delivery.
Everkleen Self-Cleaning System is Rheem's patented technology that uses the high-pressure spiraling stream.
All these self-cleaning systems are helping operating efficiency and extending the tank life, maintain high energy efficiency, maximizing the output while saving energy and money.
Note: In most cases the manufacturer's warranty does not apply if there is a heater failure due to rust, scale, and lime buildup and deposits.
If you are the owner of a tank-type water heater, you should not ignore the sediment buildup, even at its early stage. Sediment buildup is not harmful as long as water is soft, but if water is hard and neglected for some time, deposits can make the system inefficient, valves clogged, metal tank corroded and eventually leaky.
While there are some ideas how to break the buildup and remove the deposits from the tank, the easiest and safest way is to maintain (drain and flush) the unit regularly because prevention is the key.
How to fix a noisy water heater
Repair leaking water heater
Hot water heater leaking from the top
Water heater leaking from the bottom
Troubleshooting sediment buildup
Rusty water and how to fix it
Repair rotten egg odor
Water hammer solution
How to repair smelly water heater