How properly to maintain a water heater burner assembly and keep the efficiency and performance high. Find out how regular gas burner inspection and cleaning reduces the heating problems, such as no heating, not enough hot water, low performance and other.
Storage or tank-type gas water heaters are the most popular devices for water heating in North America. One of the reasons for its popularity is the simple design, reliable and easy-to-use features.
The main elements in the tank-type heaters are the gas control valve and gas burner assembly, so the regular inspection and maintenance will provide steady performance, efficient operation and years of trouble-free work.
If these elements are not working or working with the reduced capacity, the odds are that you will experience problems, uncomfortable shower and lack of hot water.
In order to understand gas burners better and solve potential problems, lets first see how they work.
Whenever you open the hot water tap, hot water leaves the tank from the upper section, through the pipes, and to the fixture, while at the same time cold water, through the dip tube gets delivered at the bottom of the tank. As the water goes down the line, the water temperature in the tank drops.
Once the thermostat senses that water is below the set temperature, it sends the signal to the gas valve to open gas, and pilot light fires the water heater burner to heat the cold water. Even if you are not using hot water, and due to the standby heat loss, the temperature inside the tank drops, and once it is below the pre-set temperature, the gas burner will come ON.
The most used way of lighting the gas burner is utilizing the standing pilot light, while other more advanced methods include the electronic or spark ignition and hot surface.
Every water heater burner, either using the natural gas or propane produces a carbon dioxide and water vapor, which is the result of gas combustion. From the water heater burner and combustion chamber, combustion by-products will, through the flue and chimney, leave the heater to the outdoors.
Most of the gas burners will burn the gas and heat the water with the efficiency of 60-70%, using the energy from the combustion chamber, while condensing water heaters, such as AO Smith Vertex or Polaris will “steal” the energy from the flue gases and increase the efficiency to 90% or more, while reducing the temperature of the flue gases.
Water heater burner assembly consists of several elements:
The thermocouple as the safety element is used to determine is the pilot flame present or not, and will shut off the gas supply to the main gas burner if the flame is absent.
TCO or Thermal Cut Off switch is an integral part of the thermocouple, and it will shut off the pilot burner and main burner when activated. The element is activated when the temperature inside of the combustion chamber increases significantly. One of the reasons for the excessive temperature is due to the flammable vapor ignition.
A gas burner is located in the combustion chamber, where, for the proper work should get sufficient supply of fresh air. If the oxygen is not available in the right amount, water heater burner will not burn the gas correctly, causing the following:
If the wrong size of the orifice is installed, it is dirty or the gas tube is unclean, the main burner flame will be too large or very small. If the burner flame floats and lifts off the port, check the orifice as it might be too big, or the pressure is high, or there are cold drafts or the flue and vent system are blocked.
Black or red granules found on the main gas burner are symptoms of the condensation, when mild acid water is dripping, which corrodes the steel and makes a sizzling noise. In a case of the excessive condensation, water is running down the flue tube and onto the main burner, putting out the pilot flame. Keep in mind that condensation is common at the time of start-up after installation and due to cold incoming water.
Also, if the water heater is cleaned and flushed periodically this will prevent sediments and lime deposits to rise up to a level when it is hard for the gas burner to heat water.
A soft blue flame is the sign of the correct gas combustion. Use the viewport at the bottom of the water heater to inspect the burner flames, at least twice a year. If you see blue tips with the yellow inner cones, it is still OK. If the flame is all yellow or with the blue and orange colors or there is sooting, something is wrong.
Every time you clean the water heater burner assembly the control knob on the gas valve has to be in the OFF position, and the main valve located beside the water heater also turned OFF.
The procedure is as follows:
Remove the outer door.
There are usually two screws holding the manifold/burner door assembly to the combustion chamber. Remove them.
Disconnect the gas valve, main burner and pilot feed line, thermocouple and pilot tube.
Remove the burner assembly from the combustion chamber and burner from the burner assembly (it is usually secured by two screws).
Visually check the burner and burner ports for any damages and clean it if it is dirty or clogged; use the hot water, soap, and soft paint brush.
Clean the rest of the burner assembly elements, including the pilot tube, flame arrestor, combustion chamber... You can also use the compressed air (vacuum) to remove any deposits from the burner and a screen.
All gas-powered water heaters today are designed with the FVIR system, which reduces the risk of the accidental fires when the flammable vapors enter the combustion chamber and are lit by the burner. Low NOx water heaters are becoming more and more popular as they are equipped with the environment-friendly gas burners that have reduced NOx emission. The perfect example is the Promax Ultra Low NOx water heater that utilizes the Enhanced Green Choice gas burner.
Nobody likes to have a broken water heater, under-performing unit, and no hot water. This is why clean and efficient gas combustion is a goal and it can be achieved only when the water heater burner assembly is properly maintained and serviced.
Keep in mind, that the gas burner operates only when there is a call for heating, and as the safety precaution it won't ignite when the pilot is not lit, when the thermostat is set too low, there is a dirt in the gas, main burner or pilot line, lack of fresh air or due to the thermostat and thermocouple malfunction.
Drain valve - How to replace
Heating elements - Buying guide, testing and replacing
Thermostats - how to set, problems, testing and replacing
How to replace an anode rod
How to replace a thermocouple
Replacing a TPR valve
Dip tube - how does it work and replacing tips